If the CJ1W-PRM21 fails to participate in this specific configuration, it will be impossible for the unit to make any data exchange. Besides this, the Omron master unit will operate under certain Microsoft Windows programs such as NT 4. The master unit has a port that connects to an RS cable which is galvanically isolated from the PLC. The dimensions of the master unit are 31mm by 90mm by 65mm 1. The configurator may also choose one of the twelve selected baud rates that range between 9.
|Published (Last):||10 June 2007|
|PDF File Size:||18.3 Mb|
|ePub File Size:||18.49 Mb|
|Price:||Free* [*Free Regsitration Required]|
Shakora It is profibus slave. I made a diagnostic to de cp and appear this error: I also programed the functions send and recv acording with the master configuration. Hello, the BF led blink fj1w the omron master, the slave appear only with the led run. Sign up for a new account pr,21 our community. All about Decentral Peripherie.
I configured in S7 project the slave parameters. I can now use diagnostic option and I can see states of plc and module. Register a new account. What about those errors? Share this post Link to post Share on other sites. Search myKnowledge The module was update to firmware V3, but I have only in step dj1w the product versions 1 and 2.
When i try to use scan option i get another error:. Edited 21 March by malyalewariat. Hello Ariel; In your diagnostic messages a few stand out, at first glance ArielP 10!! The master tell me that the slave have a invalid response. It supposed to be toolbus usb in configuration tab, and now i can use test, and go c1jw options without any errors.
Here I have que diagnostic of the cp slave. Product Support Services Forum mySupport. I uploaded the file already. Site Explorer Site Explorer. In the front of the module apeare that is the version 2. Am I missing CX-Server?
What I can do. Follow us on Twitter Youtube. Started by malyalewariat18 March. I have no idea. This contribution pfm21 helpful to 1 thankful Users dchartier.
If this is already done, it would be good to see how they have been configured. The number of bytes its going to recive and send.
Hello Ariel; You seem to have had difficulty in uploading your diagnostic information. Posted 21 March edited. I should do any thing else, Thaks. So many communication protocols to choose. Create an account or sign in to comment You need to be a member in order to leave a comment Create an account Sign up for a new account in our community. Seeing the scan returns error with DTM version 1.
Hello Daniel, Thanks for your answer. Started by malyalewariat18 March prm21 cj1w bus profibus.
Migis When i try to use scan option i pprm21 another error: Share this post Link to post Share on other sites. Hello, the BF led blink in the omron master, the slave appear only with the led run. The GSD file you will find here: The number of bytes its going to recive and send. Register a new account. I also programed the functions send and recv acording with the master configuration. It pm21 profibus slave. I can now use diagnostic option and I can see states of plc and module.
CJ1W PRM21 PDF